MANUAL TRIP DUE TO A PRIMARY TO SECONDARY LEAK GREATER THAN 30 GAL/HR
“At 1505 PST, Unit 3 entered Abnormal Operation Instruction S023-13-14 ‘Reactor Coolant Leak’ for a steam generator leak exceeding 5 gallons per day.
“At 1549 PST, the leak rate was determined to be 82 gallons per day. At 1610 PST, a leak rate greater than 75 gallons per day with an increasing rate of leakage exceeding 30 gallons per hour was established and entry into S023-13-28 ‘Rapid Power Reduction’ was performed.
“At 1630 PST, commenced rapid power reduction per S023-13-28 ‘Rapid Power Reduction’. At 1731 PST, with reactor power at 35% the Unit was manually tripped. At 1738 PST, Unit 3 entered Emergency Operation Instruction S023-12-4 ‘Steam Generator Tube Rupture’.
“At 1800 PST the affected steam generator was isolated.”
All control rods fully inserted on the trip. Decay heat is being removed thru the main steam bypass valves into the main condenser. Main feedwater is maintaining steam generator level. No relief valves lifted during the manual trip. The plant is in normal shutdown electrical lineup.
Unit 2 is presently in a refueling outage and was not affected by this event.
The licensee has notified the NRC Resident Inspector. The licensee has issued a press release.